The course was well received with 15 new PROFIBSUS Installers becoming certified. The attendees had the opportunity to do some hands-on troubleshooting on the PCC’s training rigs. They are asked to identify and correct the faults on the rigs which are typical faults that one might find on a plant. Some of these faults can be identified and corrected by visual inspection, which can only be done once you know what you are looking for – that is, by coming on training. Some faults you can only identify with the appropriate test tools, without which, they discovered, they would be shooting in the dark. Profibus test tools include the BC-600 from Softing, the NETTEST II from COMSOFT and the ProfiCore Ultra from PROCENTEC.
The training the PCC offers has to keep up-to-date with the latest technologies that are at the PROFIBUS user’s disposal. This is why ComBricks from PROCENTEC have been introduced into the troubleshooting section of this course. ComBricks allows for permanent remote monitoring of your PROFIBUS or PROFINET network and can be used a modular repeater. ComBricks are able to record messages from before and after an error occurs and email the appropriate personnel of an alarm or a potential problem. A user can log in through a web browser, potentially from home though VPN and monitor the network in real time and advise on-site personnel on what to do. For those attendees that are on standby, this is a very appealing product!
All of these devices and test tools are available from IDX.
Thank you to Dianne Williams from Cube Technologies for organising the training and to Sharmaine Dyman, The HR Coordinator for Training at Mondi who made sure that everything ran smoothly. We look forward to running training in Richards Bay soon again.
If you are in the Natal region and would like to attend a PROFIBUS Course and not have to travel to Johannesburg to do so, then Contact Dianne Williams at Cube Technologies on +27 31 764 6081 or visit their site at www.cubetech.co.za. For training in Johannesburg or on-site training, then please feel free to contact the PCC on +27 11 548 9977 or visit www.profibuscentre.co.za.
Popular posts from this blog
Last week IDX were called to site at a large commercial residence building in Pretoria, South Africa. Where our client was implementing an IoT solution for remote monitoring and control of various HVAC and power systems in the building. The control system the SI chose in this case was a Modbus enabled Industrial Micro PC called the Revolution PI. The client had Modbus sensors connected to boilers, air conditioning systems, ventilation systems and power meters. The Modbus communications between the controller and the sensors were intermittently failing due to various installation and implementation faults: 1. Earthing and Shielding Within any fieldbus communication installation, one of the requirements to ensure uninterrupted operation is to implement adequate grounding and shielding techniques. Effective grounding and Shielding help to prevent electrostatic and electromagnetic pickup, which can lead to failed communications. Some of the shielding and grounding req
Tag management of real-time data systems can prove challenging. As an industrial IT company we frequently come across the problem where tags need to be migrated from one system to another or where tags need to be synchronised and maintained between systems including historians. Generally, this ends up being a manual process, often involving Excel and much diligence and patience of the maintainer’s behalf. IDX Unifig was the first incarnation of a tool we designed with the aim to simplify the migration and management of tags between systems. The tool worked, but with as with most first editions of software tools, we could see the need for improvement and refinement of the approach used. Thus Tag Manager was born, and has become the key stone in the IDX 8 software suite. All other IDX 8 modules, such as Data Exchange, Alarms and Events and the Historian use Tag Manager to store and reference tags. The comparison result we like to see - no changes. Tag Manager employs a plug
Quick guide to get access to the P+F advanced diagnostic module via RS485 and COM converter. In order to do this, you need an RS485 converter which can convert RS485 to either ethernet or USB. I used a device from HMS (Anybus) called the Serial Server ( AB7701 ). This device connects to RS232, 422 or 485 and makes the data available over ethernet to your computer using a virtual com port. Connect the converter to the Diagnostic bus connection on the Pepperl & Fuchs fieldbus power hub 1. Once you have the com port available on your PC, Check the comport number via “manage my computer” Make sure that the FieldConnexd Diagnostic server (FDS) is running. Go to “Windows button”>“All programs” > “Pepperl+Fuchs” and start FDS control center In case the FDS is not running click onto “Start FDS” (in case it is running nothing is left to do here) click onto “Hide”. To avoid that this piece of software will be forgotten in future click onto settings and choose un