What do pizza and PROFIBUS have in common with each other? Cheese!
Bandini Cheese is a South African cheese manufacturer supplying their products to numerous pizza restaurants around South Africa. They are always striving to provide the highest quality products and this ethos can been seen in other aspects of their manufacturing process. For them, the up-time of their PROFIBUS network is critical - not only do they have expectant customers, but the very nature of the cheese making process means that batches cannot just sit around while technicians try to troubleshoot the PROFIBUS network.
Realizing this, the engineers and technicians working on the plant attended the certified PROFIBUS Engineers Course at the South African PROFIBUS Competence Centre (PCC). It was here that they heard of new innovative product called COMbricks and they became one of the first companies to implement the COMbricks solution.
Solution to what? The problem is knowing the health of the PROFIBUS network. This can be determined by looking at how many corrupted, repeated, illegal or diagnosic messages are passing through the network and of course by looking at the signal itself. COMbricks can do all of this and report on any errors before they become failures.
Bandini optimized their network by adopting a tree layout verses a linear layout. A PROFIBUS cable connects the PLC in the control room to a COMbricks Scope Repeater Module. 5 more Scope Repeater Modules are used to repeat the signal to 5 new PROFIBUS segments running to different areas of the plant, each of which loop back to a location near the COMbricks. Active terminators are used at the ends of these segments so that if a slave fails or needs to be replaced, the segment is unaffected by reflections caused by an un-powered termination. This layout makes troubleshooting much simpler.
Being able to share the reports that the COMbricks produces with experts at the South African PCC, brings the expert to the site without him having to travel there. Even a screen shot in an email can be a much quicker way of trying to diagnose what the problem is. We can quickly narrow down the problem to the segment connected to slot 7 of the COMbricks - awesome!
Popular posts from this blog
Last week IDX were called to site at a large commercial residence building in Pretoria, South Africa. Where our client was implementing an IoT solution for remote monitoring and control of various HVAC and power systems in the building. The control system the SI chose in this case was a Modbus enabled Industrial Micro PC called the Revolution PI. The client had Modbus sensors connected to boilers, air conditioning systems, ventilation systems and power meters. The Modbus communications between the controller and the sensors were intermittently failing due to various installation and implementation faults: 1. Earthing and Shielding Within any fieldbus communication installation, one of the requirements to ensure uninterrupted operation is to implement adequate grounding and shielding techniques. Effective grounding and Shielding help to prevent electrostatic and electromagnetic pickup, which can lead to failed communications. Some of the shielding and grounding req
The SG-gateway family is a current leading Smart Grid application solution, acting as a remote terminal unit for the energy market. The SG-gateway enables the remote control and management of electrical equipment in power grids, controlling and monitoring assets, processes and installations in the field. Networking and interfacing between various fieldbuses and Industrial Ethernet protocols is where this gateway shines, allowing cross interfacing between: IEC61850 (Client/Server) IEC60870-5-104 (Client/Server) Modbus TCP (Client/Server) Modbus RTU (Master/Slave) Various Serial RS232, RS485 and RS232 PROFIBUS PROFINET EtherNet/IP Here are some application examples: Transmission can also be made available via Ethernet or 3G VPN connection into your server. The SG-Gateways sports an easy web based configuration tool using a standard browser, configuring with a simple drag and drop method. Choose the right SG-gateway to suit your requ
Tag management of real-time data systems can prove challenging. As an industrial IT company we frequently come across the problem where tags need to be migrated from one system to another or where tags need to be synchronised and maintained between systems including historians. Generally, this ends up being a manual process, often involving Excel and much diligence and patience of the maintainer’s behalf. IDX Unifig was the first incarnation of a tool we designed with the aim to simplify the migration and management of tags between systems. The tool worked, but with as with most first editions of software tools, we could see the need for improvement and refinement of the approach used. Thus Tag Manager was born, and has become the key stone in the IDX 8 software suite. All other IDX 8 modules, such as Data Exchange, Alarms and Events and the Historian use Tag Manager to store and reference tags. The comparison result we like to see - no changes. Tag Manager employs a plug