IDX has been successfully running certified PROFIBUS training for the last half decade and is now starting the IDX Training Academy which will be the umbrella for other fieldbus and device training. Watch this space for future training offerings including PROFINET, MODBUS and device related training (HMS, Procentec, Softing and Comsoft). We have been providing a combined PROFIBUS/ASi course for a number of years but we have decided to give ASi a space of its own. So we are proud to introduce Actuator/Sensor Interface, otherwise known as AS-Interface (ASi), training.
The course will begin with an introduction to AS-Interface: where does it fit and when to choose it. Attendees will have a look at various topology options and network structures. The course then covers how power and data are transmitted and how the masters and slaves interact with each other. The training will cover the features, benefits and limitations of ASi as well as some safety considerations. The attendees will discover how ASi can be incorporated into higher-level network structures such as PROFIBUS.
The attendees will investigate how ASi handles data throughput in terms of speed, delay times, jitter etc. The course then looks at the interoperability of different devices from different vendors. The trainees will take a deeper look into how the ASi slave is coupled to sensors and actuators, and at the same time the trainees will be introduced to how the ASi master works. The course will cover the transmission phases for controlling data exchange, start-up procedures and addressing.
The trainer will discuss how ASi implements portions of the OSI reference model in terms of its communications system. Focus will be on the physical layer of the OSI model (cable, power, etc), the data link layer (messages, error handling, etc) and the application layer (message traces, different types of message requests/responses, etc).
On the practical side, the IDX Training Academy has developed demonstration boards where attendees will get the opportunity to build a small ASi network, giving them hands on experience on installing ASi devices. Trainees will also use handheld tools to change slave addresses and read and write values. They will also be given the opportunity to get the devices into data exchange through some fault finding.
The course will end with a basic assessment on the material covered during the course of the day and it is the hope of the IDX Training Academy that this will give the attendee the basic know-how and confidence to design, build and troubleshoot ASi networks.
For any queries, please contact us through our site www.idxonline.com
I look forward to hearing from you!
Popular posts from this blog
Last week IDX were called to site at a large commercial residence building in Pretoria, South Africa. Where our client was implementing an IoT solution for remote monitoring and control of various HVAC and power systems in the building. The control system the SI chose in this case was a Modbus enabled Industrial Micro PC called the Revolution PI. The client had Modbus sensors connected to boilers, air conditioning systems, ventilation systems and power meters. The Modbus communications between the controller and the sensors were intermittently failing due to various installation and implementation faults: 1. Earthing and Shielding Within any fieldbus communication installation, one of the requirements to ensure uninterrupted operation is to implement adequate grounding and shielding techniques. Effective grounding and Shielding help to prevent electrostatic and electromagnetic pickup, which can lead to failed communications. Some of the shielding and grounding req
In this blog, I will discuss the steps involved in getting the Netbiter to record and display values coming out of the ComAp Generator Panel, so that one can do remote monitoring and control of the generator. The Netbiter Model used in this case is the EC220 and the panel used is the InteliLite AMF 26 P. The steps followed here can be applied to any MODBUS device due to the generic nature of the Netbiter. S tep 1 - Physical Connection Check that the Control Panel has a communication module attached to the back of it. You will need to establish the medium (RS458/RS232) and the protocol spoken (MODBUS RTU/ASCII) - all of this information will come from the user manual of the generator. Finally confirm the communication settings (baud rate, parity, stop bits, etc) - these can sometimes be changed so check what they are on the actual panel. In this case, we have the following settings: MOUBUS RTU over RS232 (you'll need an external converter to convert the RS232 to RS
Hopefully this post will help you if you are having trouble finding the IP address of your Anybus X gateway. The MODBUS TCP Client Range of these gateways enable you to control a MODBUS TCP server and port that information to a whole host of different protocols such as PROFINET, PROFIBUS, DeviceNet, etc. When you get one of these units out of the box, you shouldn't have any problems searching for and configuring the gateway on your Ethernet network, but sometimes you are given a configuration that has been used in the plant already and now you need to make some changes. So what is your first step? Install and run the Anybus IPconfig tool (available on the Anybus website or on the the CD that comes with your unit). Assuming your physical Ethernet connection is intact, you should be able to scan the network for any HMS devices that are connected to the network. Tip: I would connect and Ethernet cable directly to the Gateway from the PC and disable the wireless card to