IDX has made a way for you to obtain your PROFIBUS PA certification less expensive and less time consuming. The prerequisite to attend the PROFIBUS PA engineer’s course was that you needed to be a certified PROFIBUS installer and engineer. In the past you would had to have attended and passed the PROFIBUS installers course and PROFIBUS engineer’s course before you would be allowed to attend the PROFIBUS PA engineer’s course.
This is obviously frustrating for those people that are only concerned with PROFIBUS PA. We have reengineered the course so that you no longer require the prerequisite of any previous PROFIBUS courses to attend the PA course. The standalone course will still feature the PA content over the normal 3 day period but will also include 2 days of PROFIBUS up skilling so that you are capable and confident to move on to the PA component of the course. The stand alone course will run for a duration of 5 days.
If you have already completed the PROFIBUS engineers course, you will only need to attend the 3 day PA portion of the course at a reduced rate.
Please view our schedule for the course dates.
Popular posts from this blog
Last week IDX were called to site at a large commercial residence building in Pretoria, South Africa. Where our client was implementing an IoT solution for remote monitoring and control of various HVAC and power systems in the building. The control system the SI chose in this case was a Modbus enabled Industrial Micro PC called the Revolution PI. The client had Modbus sensors connected to boilers, air conditioning systems, ventilation systems and power meters. The Modbus communications between the controller and the sensors were intermittently failing due to various installation and implementation faults: 1. Earthing and Shielding Within any fieldbus communication installation, one of the requirements to ensure uninterrupted operation is to implement adequate grounding and shielding techniques. Effective grounding and Shielding help to prevent electrostatic and electromagnetic pickup, which can lead to failed communications. Some of the shielding and grounding req
In this blog, I will discuss the steps involved in getting the Netbiter to record and display values coming out of the ComAp Generator Panel, so that one can do remote monitoring and control of the generator. The Netbiter Model used in this case is the EC220 and the panel used is the InteliLite AMF 26 P. The steps followed here can be applied to any MODBUS device due to the generic nature of the Netbiter. S tep 1 - Physical Connection Check that the Control Panel has a communication module attached to the back of it. You will need to establish the medium (RS458/RS232) and the protocol spoken (MODBUS RTU/ASCII) - all of this information will come from the user manual of the generator. Finally confirm the communication settings (baud rate, parity, stop bits, etc) - these can sometimes be changed so check what they are on the actual panel. In this case, we have the following settings: MOUBUS RTU over RS232 (you'll need an external converter to convert the RS232 to RS
Hopefully this post will help you if you are having trouble finding the IP address of your Anybus X gateway. The MODBUS TCP Client Range of these gateways enable you to control a MODBUS TCP server and port that information to a whole host of different protocols such as PROFINET, PROFIBUS, DeviceNet, etc. When you get one of these units out of the box, you shouldn't have any problems searching for and configuring the gateway on your Ethernet network, but sometimes you are given a configuration that has been used in the plant already and now you need to make some changes. So what is your first step? Install and run the Anybus IPconfig tool (available on the Anybus website or on the the CD that comes with your unit). Assuming your physical Ethernet connection is intact, you should be able to scan the network for any HMS devices that are connected to the network. Tip: I would connect and Ethernet cable directly to the Gateway from the PC and disable the wireless card to