When configuring an Anybus Gateway device, some of the configurations need to be downloaded using a COM Transport path. Below is a description of how to configure a COM Transport path.
1. When the Transport Path Dialog appears, Select the Serial Tab.
2.Click the "Create" button.
3. Once you click create, you will be presented with the types of transport paths. Select the "COM-Port Transport Provider".
4. You need to give the Transport path a name. If you are planning on using multiple COM ports, make sure the name helps you select the correct COM port when configuring devices (i.e. You could name the transport path "COM 1 Transport Path" so that you know which COM port it is tied to)
5.Once you have named the Path, Select the COM Port.
6. Now that you have configured your Transport Path, you can select OK to download your configuration.
I trust this will help you get your Anybus device configured correctly.
For any questions or comments please feel free to contact us.
Popular posts from this blog
The Netbiter® device along with its ArgosTM web service technology is becoming increasingly popular in South Africa. Already it has been implemented at numerous sites for monitoring water treatment rigs, heavy machinery and other metering equipment. Very quickly the user is able to connect some IO or MODBUS devices to the Netbiter® and view and control these values through a web-based graphical dashboard. The user is able to see the current state of their system, view historical data and even receive alarms from their system. No programming required! This is all done through the secure Netbiter ArgosTM Web Interface. It is a very powerful way to monitor a MODBUS device over the Internet and by using the IO Extender cards, the user is able to switch relays and monitor additional digital and analogue IO though a web browser. Netbiter® is truly a complete package that provides one of the most flexible solutions to monitor control devices over The Internet. Furthermore, as of Marc
Last week IDX were called to site at a large commercial residence building in Pretoria, South Africa. Where our client was implementing an IoT solution for remote monitoring and control of various HVAC and power systems in the building. The control system the SI chose in this case was a Modbus enabled Industrial Micro PC called the Revolution PI. The client had Modbus sensors connected to boilers, air conditioning systems, ventilation systems and power meters. The Modbus communications between the controller and the sensors were intermittently failing due to various installation and implementation faults: 1. Earthing and Shielding Within any fieldbus communication installation, one of the requirements to ensure uninterrupted operation is to implement adequate grounding and shielding techniques. Effective grounding and Shielding help to prevent electrostatic and electromagnetic pickup, which can lead to failed communications. Some of the shielding and grounding req
In this blog, I will discuss the steps involved in getting the Netbiter to record and display values coming out of the ComAp Generator Panel, so that one can do remote monitoring and control of the generator. The Netbiter Model used in this case is the EC220 and the panel used is the InteliLite AMF 26 P. The steps followed here can be applied to any MODBUS device due to the generic nature of the Netbiter. S tep 1 - Physical Connection Check that the Control Panel has a communication module attached to the back of it. You will need to establish the medium (RS458/RS232) and the protocol spoken (MODBUS RTU/ASCII) - all of this information will come from the user manual of the generator. Finally confirm the communication settings (baud rate, parity, stop bits, etc) - these can sometimes be changed so check what they are on the actual panel. In this case, we have the following settings: MOUBUS RTU over RS232 (you'll need an external converter to convert the RS232 to RS