IDX has made a way for you to obtain your PROFIBUS PA certification less expensive and less time consuming. The prerequisite to attend the PROFIBUS PA engineer’s course was that you needed to be a certified PROFIBUS installer and engineer. In the past you would had to have attended and passed the PROFIBUS installers course and PROFIBUS engineer’s course before you would be allowed to attend the PROFIBUS PA engineer’s course.
This is obviously frustrating for those people that are only concerned with PROFIBUS PA. We have reengineered the course so that you no longer require the prerequisite of any previous PROFIBUS courses to attend the PA course. The standalone course will still feature the PA content over the normal 3 day period but will also include 2 days of PROFIBUS up skilling so that you are capable and confident to move on to the PA component of the course. The stand alone course will run for a duration of 5 days.
If you have already completed the PROFIBUS engineers course, you will only need to attend the 3 day PA portion of the course at a reduced rate.
Please view our schedule for the course dates.
Popular posts from this blog
Last week IDX were called to site at a large commercial residence building in Pretoria, South Africa. Where our client was implementing an IoT solution for remote monitoring and control of various HVAC and power systems in the building. The control system the SI chose in this case was a Modbus enabled Industrial Micro PC called the Revolution PI. The client had Modbus sensors connected to boilers, air conditioning systems, ventilation systems and power meters. The Modbus communications between the controller and the sensors were intermittently failing due to various installation and implementation faults: 1. Earthing and Shielding Within any fieldbus communication installation, one of the requirements to ensure uninterrupted operation is to implement adequate grounding and shielding techniques. Effective grounding and Shielding help to prevent electrostatic and electromagnetic pickup, which can lead to failed communications. Some of the shielding and grounding req
Tag management of real-time data systems can prove challenging. As an industrial IT company we frequently come across the problem where tags need to be migrated from one system to another or where tags need to be synchronised and maintained between systems including historians. Generally, this ends up being a manual process, often involving Excel and much diligence and patience of the maintainer’s behalf. IDX Unifig was the first incarnation of a tool we designed with the aim to simplify the migration and management of tags between systems. The tool worked, but with as with most first editions of software tools, we could see the need for improvement and refinement of the approach used. Thus Tag Manager was born, and has become the key stone in the IDX 8 software suite. All other IDX 8 modules, such as Data Exchange, Alarms and Events and the Historian use Tag Manager to store and reference tags. The comparison result we like to see - no changes. Tag Manager employs a plug
Quick guide to get access to the P+F advanced diagnostic module via RS485 and COM converter. In order to do this, you need an RS485 converter which can convert RS485 to either ethernet or USB. I used a device from HMS (Anybus) called the Serial Server ( AB7701 ). This device connects to RS232, 422 or 485 and makes the data available over ethernet to your computer using a virtual com port. Connect the converter to the Diagnostic bus connection on the Pepperl & Fuchs fieldbus power hub 1. Once you have the com port available on your PC, Check the comport number via “manage my computer” Make sure that the FieldConnexd Diagnostic server (FDS) is running. Go to “Windows button”>“All programs” > “Pepperl+Fuchs” and start FDS control center In case the FDS is not running click onto “Start FDS” (in case it is running nothing is left to do here) click onto “Hide”. To avoid that this piece of software will be forgotten in future click onto settings and choose un